Why is my boiler making a whistling / kettling noise?
Answered by South Yorkshire Heating
29th May 2020
South Yorkshire Heating answered the question "Why is my boiler making a whistling / kettling noise?"
If it does it all the time whether in central heating or hot water it is possible that the main heat exchanger is partially blocked. If it does it only on hot water it could be the plate heat exchanger is partially blocked. It really could be any number of issues but perhaps these are the most common. Ut would be best to get it professionally looked at.
Answered by Macaulay Ferguson Ltd
11th May 2020
Macaulay Ferguson Ltd answered the question "Why is my boiler making a whistling / kettling noise?"
Whistling or Kettering in a boiler is quite often due to a build up of debris restricting flow through the boiler. The water does not circulate properly and therefore makes a noise like a kettle. Cleaning the main heat exchanger, pump and associates flow and return water ways may help to reduce the noise and increase efficiency.
Answered by DLM GAS Ltd
25th June 2019
DLM GAS Ltd answered the question "Why is my boiler making a whistling / kettling noise?"
A kettling noise from the boiler is down to localised boiling within the heat exchanger. Heat is not dissipating from the heat exchanger and the flow rate is inadequate. A slow or failed pump could cause this, a restriction or blockage in the primary circuit, or a blocked heat exchanger could all contribute to this fault. Here at DLM Gas, we have over 16 years of experience as a breakdown engineer and have attended to many jobs with this fault, we would advise our customers to contact a gas safe registered business like DLM Gas to attend for a full diagnosis and fix.
Answered by Gas On Sea
24th May 2019
Gas On Sea answered the question "Why is my boiler making a whistling / kettling noise?"
If your boiler is making a whistling or kettle noise this could be due to sludge within the heat exchanger, the lack of circulation within the heat exchanger will cause the boiler to overheat and boil the system water air lock is another cause of this where steam will occur within the heat exchanger. BoilerOne recommend you consult a gas safe registered engineer to diagnose the problem.